- Mini Split
- Heat Pumps
- Water Heaters
- Portable AC
- Shop by BTU
This 24000BTU Ductless Air Conditioner by Senville is one of the most advanced and high-end split units on the market. Providing you with a variety of features including, SEER 20, 24000BTU Cooling, 2400BTU Heat Pump, Turbo Mode, Ionizing Air Filter, Dehumidification, Timer Function, Follow Me Function and much more.
With SEER Ratings as high as 20, the Senville Aura surpasses many of the top name brands when it comes to efficiency. Enjoy the benefit of a cool climate controlled room, with a simple and easy to install air conditioner. Additionally, the 24000BTU Senville Aura offers you one of the quietest split air conditioning systems on the market, with minimal audible noise, ensuring the most comfortable overall experience.
The Senville Aura Series is also fully certified by Energy Star for the highest levels of energy efficiency. With ultra energy efficient air conditioners, you can expect to save upwards of 40% on your energy costs annually. This model makes a great companion for anyone looking to cool and/or heat their home or business, while minimizing running costs in the long-term.
Senville is proud offer one of the most advanced heating and cooling systems in the world. Our Ultra-Inverter Technology, allows our mini split systems to provide cooling and heating at up to -22F, with up to 75% efficiency, which means you won't experience any additional cost overages on your energy as temperatures go lower. Now available on all of our AURA Series models, your Ultra Inverter system will provide you with cooling and heating, all year round, even in the coldest climates. Û¬
Also included on this ductless system are a variety of features including self-cleaning, leak detection, and diagnostic display, all designed to ensure a proper running system, that will last a lifetime. Enjoy peace of mind, knowing that your air conditioner will warn you of any potential problems, allowing for proper maintenance and a climate control system that functions at it's highest efficiency.
Senville has long manufactured their air conditioners with an emphasis on energy efficiency and affordability. Technology like its inverter compressor, results in drastic reduction of energy usage, ultimately making it one of the most efficient systems with Inverter Technology. It's technology like this that helps the ductless system to reach such high SEER ratings. Opt for a split system with Inverter Technology to ensure that you are minimizing your energy costs.
All Senville models are backed by a comprehensive 7 year warranty designed to protect your purchase. All warranty claims are processed by the North American Headquarters of Senville, ensuring the highest levels of customer support and satisfaction. This 7 year warranty offers coverage on the compressor and a 2 year warranty on other parts. You can rest assured knowing that your purchase will be protected for up to 7 years, and we know that we are providing you with the highest quality product available.
Senville air conditioners include a complimentary installation kit, designed to ease installation as well as minimize installation costs. These units come pre-charged with R410A refrigerant and include the necessary piping for installation and hook up. Many inferior split units, may not include these parts, which eventually adds to your costs. Our Senville models come equipped and ready for installation from the moment your arrive at your door, with minimal additional cost.
*Important Note: Installation kit does not include wiring harness or electrical wiring. Standard electrical wiring can be provided by your installer, or can be purchased at a local hardware store. Please refer to technical specifications for wire sizes and specifications.
|Style||Ductless Mini Split AC With Heat Pump|
|Refrigerant Pre Charge||25 Ft.|
|Cooling Capacity||24000 BTU|
|Heating Capacity||24000 BTU|
|Air Flow||794 H / 647 M / 500 L CFM|
|Power Supply||208-230 V / 60 Hz, 1 Ph|
|Input Power||1920 W (cooling) / 2500 W (heating)|
|Input Current||8.4 A (cooling) / 10.9 (heating)|
|Sound Level||47.5/44/36.5 dB (indoor unit) / 60 dB (outdoor unit)|
|Moisture Removal||2.5 L / hr|
|Min Operating Temperature||- 30 C / - 22 F|
|Net Weight||40 lbs (indoor unit) 135 lbs (outdoor unit)|
|Dimensions||46.69x10.16x13.39 in (indoor unit) 37.24x16.54x31.89 in (outdoor unit)|
|Warranty||2 Years on Parts / 7 Years on Compressor|
|Connection Wiring (Indoor/Outdoor)||16AWG-4 Stranded, Unshielded|
|Connection Wiring (Power Supply)||10-3 Gauge|
I have installed this product many times now and found it to be very worth the money spended. Works great., quiet . Clean and affordable.. found the staff very friendly to deal with. They go well out of their way to make sure you get what you order and the it arrives intack and on time. No hesitation in buying this Product in the future has it is well worth the money spend
Dave Billard Burgeo Nl on 2017 Aug 19th
I installed this unit a few days ago and so far, it is very impressive! You can barely hear it and it heats and cools very fast. It has no problem to maintain a set temperature in my 1,300 sqf home.
The installation was a little troublesome. I am a handy man and when I ordered this unit without having any experience on the installation, I thought I will have no problem installing it if an installation instruction is included (which there was). Once I had the system installed, I realized I need a "manifold Gage" and vacuum pump for the "evacuation" of the lines. I had no idea such tools are needed. I checked some local plumber supply stores and realized these tools sell for $1,400 (there are cheaper ones to be found online but with no experience with these tools, I do not know what quality features to look for and scared away). I ended up hiring a plumber for this part of the installation which added $320 to my cost. Had I known this upfront, it still would not have me change my mind about the purchase but I would have had the chance to organize the installation better. Plumbers in our area are very busy and not able to come right away when first contacted. Therefore, I had to wait over a week for a plumber to show up after I had the unit installed and realized that I do need a plumber. Steffen on 2017 Jul 31st
This unit runs really super quiet!!! I hooked up a power meter to keep track of power usage and so far it seems super efficient. Full blast cooling pulls about 1350W! Less than a hair dryer. Once it gets closer to set point and idles back to maintain temp it pulls 560W, just 20W more than the summer fan on my furnace. Once it reaches the desired temp the air handler fan on low idle pulls just 15w. The unit completely off consumes 8w. Overall really, really happy with this unit, especially for the installed cost. Did the electrical and mechanical installation myself, except for the commissioning I left to a licensed HVAC repair man; vacuum evacuation, leak test, line purge and freon release. He said this unit was very well constructed, and was impressed that it had a scroll compressor at this price. Of course i needed a longer line set than 25ft, so he cut and flared a 30ft set down to 28ft. I got the 30ft line set off ebay because with the 5/8" vapour line all the local plumbers / parts suppliers treated me like an idiot when i asked for them, one also told me to scrap this unit and buy a $5k Carrier, yeah right buddy. I will be keeping track of this units efficiency/consumption in a spreadsheet, to see how much propane it will save me in winter and where the economic the balance point is using the heatpump.
The outdoor unit is very quiet, you have to walk over to it to see if it is on.
Ok now the things i don't like, improvements to be made. Wish it would have a display led on the air handler for heat mode and also dry mode which it does not. Wish it had dry contacts or wifi control for Nest integration which it does not. Wish Airpatrol was not so terribly annoyingly buggy interfacing with this unit. I wish the temperature display led's on the unit could be centered, kinda looks goofy offset to the left. The neoprene seal in the senville line set kit is junk, wouldn't stick just tossed it, get yourself some proper hvac duct seal from the hardware store. But really that's it, Overall a really impressive machine for the price, I am quite happy.
I hope to review this unit again after a winter in Alberta! Tynell on 2017 Jul 30th
just got it installed today at last .by a pro .was a big job and the units seem to be whisper quite with all the bells and whistles you can think of .i would change where the wiring goes in to the outdoor unit .a plate would be much better than the two holes through the cover and bigger flares on the line ends.we redid the flares. other than that it`s wonderful so far .hope it stands up well is all . only time will tell if i saved money or threw it away i guess.$ 560 ca to install and the electrician was very reasonable . thanks m. buckley on 2017 Apr 12th
installation was easy lucioen roy on 2017 Apr 5th